Duplex Service Drop Wire meets or exceeds the following ASTM specifications:
B-230 Aluminum Wire, 1350-H19 for Electrical Purposes.
B-231 Aluminum Conductors, Concentric-Lay-Stranded.
B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR).
B-399 Concentric-Lay-Stranded 6201-T81 Aluminum Alloy Conductors.
B498 Zinc-Coated Steel Core Wire for Aluminum Conductors, Steel Reinforced (ACSR).
Duplex Service Drop cable meets or exceeds all applicable requirements of ANSI/ICEA S-76-474.
Duplex Service Drop Wire consists of Concentric strand or compressed 1350-H19 conductor, polyethylene or crosslinked polyethylene insulation, concentric strand AAC, ACSR, or 6201 alloy neutral messenger.
Duplex service drop wire is used to supply 120 volt aerial service for temporary service at construction sites, outdoor or street lighting. For service at 600 volts or lower at a conductor temperature of 75°C maximum for polyethylene insulated conductors or 90°C for crosslinked polyethylene (XLP) insulated conductors.